FRP Waste Gas Purification Tower/ Gas Scrubbers
|FOB Unit Price:||US $1,000 US $500|
|Purchase Qty. (Pieces)||FOB Unit Price|
|Production Capacity:||10 Set Per Month|
|Transport Package:||by Container|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: ZLRC-F
- Application: Chemical Equipment, Industry
- Surface Treatment: Smooth
- Trademark: ZLRC
- Origin: Beijing
- Name: FRP Purification Tower
- Color: According to The Requirements
- Warranty: 1 Year
- Specification: CE
- HS Code: 39269090
Acid gas purification tower series ZJP-X is made of GRP and PVC. The outer surface of the tower adopts water-tolerant and anti-aging gel coat resin with the thickness above 0.5mm. Between the inner and outer surfaces is alkali-free wax-free untwisted wove roving as the anti-aging transition layer. Its resin content is more than 75%. The quantity of the layers meets the technical standard. The resin content is up to 60~70% to ensure the reliability of the tower strength.
The purification tower is made of a circular tower and flanges by sectional connection. The concrete structure consists of liquid storage tank, air inlet section, two spray sections, cyclone plate, air outlet hood and other components. The characteristics of the purification tower are: convenient production, easy installation and maintenance, high strength, small footprint. Double fillers and sprays are used to make full contact of gas and liquid and to improve the purification efficiency. The tower is equipped with a glass fiber reinforced plastic centrifugal fan and a plastic or stainless steel water pump. When purified air quantity is more than 10,000 cubic meters, two water pumps can meet the design requirement.
Purification tower body:
1. Composite GRP liquid storage tank, dosing tubes, filtrating device on pipette, composite GRP air inlet section.
2. The first, second liquid discharge sections are made of a row of Y-1 shape nylon nozzles, Pall ring filter and PMMA viewing holes.
3. The cyclone plate improves the effect of retaining water.
4. FRP hood cover.
5. F4-72 type FRP centrifugal fan.
6. Plastic or stainless steel centrifugal pump.
7. Other accessories such as plastic pipe valves, fixing bracket, detection ladder, inlet pipe, etc. The user can customize during ordering.
Purification tower series ZJP-X components:
outlet hood cover, cyclone plate, filler layer, nozzle, viewing hole, inlet pipe, centrifugal fan, liquid discharge tube, liquid level indicator, liquid storage tank, valve, pipette, centrifugal water pump
Overall and installation dimensions Unit: mm
Specifications of purification tower
|Design air quantity (m³/h)||1500||3000||5000||7500||10000||20000||30000||40000||50000|
|FRP centrifugal fan||Model F4-72||No3.2||No4||No4||No4.5||No4.5||No8||No10||No12||No12|
|Air quantity (m³/h)||1637||3566||5315||7947||9440||17400||27250||38600||47000|
|Air pressure (Pa)||1110||1920||1480||2080||1680||1480||1220||1410||1760|
|Anti-acid water pump||Model||50FS-25||50FS-25||50FS-25||50FS-25||50FS-25||50FS-25||50FS-25||50FS-25||50FS-25|
|Pump head (m)||25||25||25||25||25||35||35||35||35|
|The initial acid mist concentration||HCL mg/m³||< 400|
|H2SO4 mg/m³||< 300|
|HNO3 mg/m³||< 1000|
|Absorption efficiency||HCL mg/m³||91 ~ 99|
|H2SO4 mg/m³||92 ~ 98|
|HNO3 mg/m³||93 ~ 96|
|Neutralization solution concentration %||2 ~ 6|
|Purification tower resistance (Pa)||400|
Installation and usage notice:
1 The device should be installed on the concrete foundation of more than 100mm above the ground. The concrete foundations of pump and fan should be made separately by request.
2 Be careful during transportation and installation. Don't damage the body and components of the equipemnt.
3 When the device is delivered, we will adopt segmental packing and shipping depending on the circumstances. We will sent person to the site to install and commiss the device.
4 If the device is installed and works outdoors, the user should prevent the pool at the bottom of device from freezing in winter
5 The device has liquid level mark of the pool at the bottom of the device. Before use inject the absorbing liquid according to the level mark. During use pay attention to add absorbing liquid.
6 When using the device, first open the circulating pump for 2-3 minutes, then switch on the blower. After use first stop the blower for 1-2 minutes, then stop the circulating pump.
7 Check acidity of the liquid in the pool at the bottom of the tower and gas purification degree in the exhaust vent periodically. If the results can't meet the standards, replace the absorbing solution in the pool
8 Maintain the device every year and a half to two years. Check and clean the sprinkler and packing.